View and Download Eaton installation and operation manual online. 20/30 kva. UPS pdf manual download. CAUTION: REFER TO OPERATOR’S MANUAL – Refer to your operator’s manual for . Figure 1 shows the Eaton UPS UPS and an optional Extended. © Eaton Corporation. All Rights contained in this manual, but no liability can be accepted for any errors or omission. Figure 5 Powerware kVA and 40 kVA layout: 1:Graphical LCD; 2:XSlot-1; 3:XSlot-2; 4:Fans;. 5:Input.
|Published (Last):||7 August 2017|
|PDF File Size:||18.89 Mb|
|ePub File Size:||10.94 Mb|
|Price:||Free* [*Free Regsitration Required]|
93355 is a registered trademark of Greenlee Textron. Modbus is a registered trademark of Schneider Automation. These limits are designed to provide reasonable protection against harmful interference when the equipment is operated in janual commercial environment. Special Symbols The following are examples of symbols used on the UPS or accessories to alert you to important information: During brownouts, blackouts, and other power interruptions, batteries provide emergency power to safeguard operation.
With the Eaton UPS, you can safely eliminate the effects of electrical line disturbances and guard the integrity of your systems and equipment. Introduction Providing outstanding performance and reliability, the Eaton UPS’s unique benefits including the following: Online UPS design with pure sine wave output.
The UPS filters and regulates incoming AC power and provides consistent power to your equipment without draining the battery. UPS from virtually any location within the facility. You can install multiple RMPs at remote locations to increase your monitoring capabilities.
Introduction This page intentionally left blank.
Eaton 9355 Installation And Operation Manual
Keep unauthorized personnel away from batteries. Proper disposal of batteries is required. Refer to your local codes for disposal requirements. Never dispose of batteries in a fire.
Batteries may explode when exposed to flame. Ne jamais jeter les batteries mabual feu. L’exposition aux flammes risque de les faire exploser.
EATON INSTALLATION AND OPERATION MANUAL Pdf Download.
Consulte las normas locales para conocer los requisitos pertinentes. Safety Warnings This page intentionally left blank. From Front of Cabinet 36″ Lift the door up and off the cabinet. To replace the door: Insert the door notches into the slots on the bottom of the cabinet. Secure the door latches. Place the door on the bottom hooks of the EBC. Replace the two door screws. Be sure to retain the rear shipping bracket and hardware for later re-assembly if you plan to permanently mount the cabinet.
M10 Bolts M8 Screws Figure 4. Remove the three M10 bolts securing the rear shipping pad to the pallet and remove the shipping pad see Figure 5.
M10 Bolts Shipping Pad Figure 5. Remove the two M10 bolts securing the front shipping bracket to the pallet and remove the bracket. M10 Bolts M8 Screws Figure 6.
mwnual Slowly roll the cabinet toward the rear of the pallet. Once the pallet tilts, continue rolling the cabinet down the pallet until the cabinet touches the floor see Figure 8. Roll the 935 to the desired location. If you have two Options Cabinets, remove the three circular knockouts on the left side of the first Options Cabinet.
Install ewton bushings supplied in the circular knockouts of the adjacent cabinet. Install the other ground strap between the front panels of the adjacent cabinets as shown in Figure Repeat Steps 11 through 13 for each cabinet. Replace the front door of all cabinets. Joining the Manula This page intentionally left blank. To accommodate the feature of easy system expandability, it is recommended that initial installation of the Eaton UPS contain wiring to support the maximum capacity of the UPS cabinet.
Switch off utility power to the distribution point where the UPS or Options Cabinet will be connected. Be absolutely sure there is no power.
Reinstall the UPS conduit landing box in the reversed position see Figure Replace the UPS 935 door see page Reinstall the UPS wiring access cover. Reinstall the UPS conduit landing box in the reversed position see Figure 14 on page Reinstall the UPS connections insulator. Replace both Options Cabinet front doors see page Cabinet with an input isolation transformer, the input neutral is supplied by the input isolation transformer. DO NOT overtighten the screws; be sure to use the specified tightening torque values shown in Table 1.
The two input neutral terminals are jumpered together; use either one of these terminals to make the input neutral connection. The two output neutral terminals are jumpered together; use either one of these terminals to make the output neutral connection. Electrical Installation Figure Extended Battery Eatpn Installation This page intentionally left blank.
EATON USER MANUAL Pdf Download.
Permanent Mounting Installation Figure Maual the control terminal cable s through the middle of the fan section and secure in the cable clips. Reinstall the communication wiring access plate.
Replace eatob UPS front door. X-Slot cards allow the UPS to communicate in a variety of networking environments and with different types mxnual devices. The Eaton UPS does not detect plug-and-play hardware. Figure 42 shows an RMP. Figure 43 shows the enclosure dimensions and cable exit openings. See Figure 44 and Figure 45 for plug-in terminal block locations.
NOTE Conduit and wiring supplied by the customer. UPS or power information. If there is a power outage and the Eaton UPS battery power becomes low, LanSafe software can automatically shut down your computer system to protect your data before the UPS shutdown occurs.
The pins must be shorted with maximum resistance of 10 ohm to activate the specific input. See Figure 46 on page 60 for the polarity and verify these connections if polarity control is required. If active, the UPS knows that input is fed from the generator. Bypass is disabled; the automatic battery test is disabled. External Transformer Overtemperature This option is not used. Remove the communication wiring access plate from the UPS rear panel and punch a hole in it using a Greenlee punch or similar device see Figure Install conduit for the communication wiring.
Communication Wiring Access Plate Figure Maunal the wiring through the conduit from the communication wiring access plate to the opening between the two X-Slot communication bays on each UPS see Figure Route the pull-chain wiring through the middle of the fan section and secure in the cable clips for each UPS see Figure Reinstall the communication wiring access plate on each UPS.
Parallel Communication This page intentionally left blank. It provides useful information about the UPS itself, load status, events, measurements, and settings see Figure Disabled after initial startup Initial Startup Startup and operational checks must be performed by an authorized Eaton Customer Service Engineer, or the warranty terms as specified on page 89 become void.
This service is offered as part of the sales contract for the UPS. Press any button on the front panel display to activate the menu options. Switch on utility power where the UPS is manyal. The load is now powered by utility power. Switch off utility power where the UPS is connected.
This section describes shutting down and restarting UPSs in a parallel system. The UPS goes to Bypass mode for five seconds, and then the indicator illuminates. Each UPS should be in Normal mode. Press the button until the Eaton logo or Eaotn screen appears. Operation This page intentionally left blank. Change the batteries approximately every five years. Turn the maintenance bypass switch to the UPS position to return to Normal mode.
Eaton 9355 User Manual
Verify the rear fan is running. The UPS is now powering the load. Press the button to select the Go to Normal Mode option.